Coating Specification for Aircraft Maintenance Hangar: Barksdale Air Force Base
NAVAL FACILITIES ENGINEERING COMMAND PORT HUENEME CA PORT HUENEME United States
Pagination or Media Count:
A hangar floor condition assessment in accordance to the Naval Facilities Engineering Service Centers NFESC Users Guide titled Condition Assessment and Coating Recommendations for Aircraft Maintenance Hangars UG - 2036 - SHR is required prior to coating the hangar. A thin film coating system may be applied to floor surfaces if the hangar displays the following condition assessment results 1 Smooth concrete surface texture, 2 Average moisture vapor emission rate 3.0 lbs24 hours, 1000 ft2, 3 Average concrete surface strength 200 psi, and 3 Average surface depth of hydrocarbon contamination 38. A thin film coating system may be applied to floors with a coarse surface texture, however the concretes surface texture may mirror through the coating system to decrease aesthetics. Installation costs 3.00 - 4.25ft2. Thickness 16 mils. Approximate service life Overcoating at 4 years. Benefits Low cost, fast installation, and average applicator skill. The Thin Film Coating System specification is enclosed in Appendix A.
- Ceramics, Refractories and Glass
- Coatings, Colorants and Finishes